Lighting Audit Helps Furniture Warehouse Achieve 72% Lighting Energy Reduction.
A leading furniture wholesaler was looking for simple metal halide lamp replacements for its 140,000 square foot warehouse lighting in Southwest Atlanta. Instead, it leveraged a comprehensive energy audit from Atlanta Light Bulbs’ Energy Solutions (ALBES) division to achieve better performance, reduced Co2 emissions and 72% lighting energy savings via a one-for-one High Bay LED fixture and lamp retrofit.
“The goal for the project was to deliver energy efficiency, meaning delivering the same (or more) services for less energy,” said Norah Silva, ALBSES Energy Solutions Specialist. “According to the EPA, warehouses on average use 37% of their energy consumption for lighting, so the potential savings on projects like this are very significant.”
As a first step, an ALB Energy Solutions consultant walked through the entire facility to inventory all warehouse lighting. He supplemented that with a detailed interview with the facilities manager to understand operating hours, loads, and to estimate what portion of utility electrical bills derived from lighting. Data was captured on a proprietary software application via an ipad and uploaded to the cloud for a comprehensive lighting energy analysis.
ALB Energy Solutions recommended high efficiency Aluminum 120 watt LED high bay fixtures to replace the existing 400 watt metal halide fixtures. An LED payback report was delivered which outlined annual costs for lighting, cooling, and maintenance, as well as the time frame for ROI. The benefits of the Georgia Power Rebate program for energy efficient lighting were introduced, and ultimately ALB Energy Solutions filed the $19,760 Georgia Power Commercial rebate paperwork also for the client.
[divider][image style=”no-style” position=”below” src=”http://solutions.atlantalightbulbs.com/wp-content/uploads/2014/01/titan-pic-e1418746466772.jpg”][list type=”circle”]Before (Highbay Metal Halide 400w) / After (LED Retrofit Fixture 120w)
[/list][divider][list type=”circle”]The advantages of the LED retrofit approach were numerous:
- Long life: Average Lamp Life of 120 watt LED is 100,000 hours, while 400 watt metal halide lamp life is only 18-20,000 hrs.
- Lumen output: LED lamps do not degrade over time. Although the initial lumen output of a metal halide fixture may be quite high, metal halide fixtures are known for their poor lumen maintenance. The average 400 watt metal halide fixture emits only 65% of its initial lumens by the time it hits mean lamp life, and as low as 40% of its initial lumens by the end of lamp life.
- Lower Maintenance: long life LED minimizes replacement and maintenance costs, as well as safety concerns associated with employees having accidents while on lifts or ladders.
- Excellent Color Rendering: LED clear, crisp, UV free light and even beam distribution provides better illumination and fewer shadows for employees who are stocking shelves or working in aisles.
- Cold Start: LED operates from a cold start, enabling energy efficiency when coupled with occupancy sensors. Metal halides require a warm up period, making it inconvenient to use frequent on-offs to achieve energy savings.
[/list][divider][diagram type=”line” title=”Annual Energy Use Comparison”][skill title=”Previous Annual 303,899 kWh” amount=”100″ color=”#1a5eab”]
[skill title=”New LED Retrofit Annual 85,884 kWh” amount=”28″ color=”#5db65f”]
[/diagram][divider][image style=”no-style” position=”below” src=”http://solutions.atlantalightbulbs.com/wp-content/uploads/2014/02/30Cars1.png”][/vc_column][/vc_row]